Register to reply 
Sequence components in fault study 
Share this thread: 
#1
Jun2214, 09:33 AM

P: 8

Hi all! I am currently learning fault study in power systems.
To my understanding In any network (symmetrical or unsymmetrical) , there would be 3 components positive sequence component, negative sequence component and zero sequence component. Question: For generators and transformers , would synchronous reactance mean/signify its positive sequence reactance? It would be very helpful if an explanation about the definition and differentiation among: subtransient, transient and synchronous reactance be provided. A prompt reply from any user is much appreciated. :) 


#2
Jun2214, 10:07 AM

P: 8

btw, please and thank you!



#3
Jun2214, 12:40 PM

PF Gold
P: 372

Yes the synchronous reactance is the positive sequence reactance. It is only useful directly when modelling lines, because generators and transformers are not modelled (usually) by a lumped reactance. Good treatment is given in 'Power system analysis' by Grainger & Stevenson. I could be corrected but I think page 460 describes how 3 phase transformers are modelled for fault conditions based on transformer type. For synch. Generators without grounded neutral, the pos. and neg. sequence diagrams can be modeled by the synch reactances of the machine. If the neutral is ungrounded, the zero sequence diagram is opened at that point, too. If the neutral is grounded through a a reactance, the zero sequence diagram has to be analyzed with 3 x the grounding reactance in series with the machine reactance.
It's a lot to describe briefly, see Grainger. 


#4
Jun2314, 01:43 AM

P: 45

Sequence components in fault study
As per IEC 609090: usually the positivesequence reactance and negativesequence reactance are the same:
for synchronous machine X2=~X1=X”d [saturated is less then unsaturated]. If X”d<>X”q then X2[negativesequence]=(X”d+X”q)/2 For 2 windings transformers X1=X2=XT [at the main position of the onload tapchanger] XT=sqrt(ZT^2RT^2) ZT=uk%/100*Vrat^2/Strf uk% =shortcircuit voltage of transformer Vrat=Rated voltage Strf=rated apparent power of the transformer. 


#5
Jun2314, 02:27 AM

P: 8




#6
Jun2314, 02:30 AM

P: 8




#7
Jun2414, 02:19 AM

P: 8




#8
Jun2414, 07:52 AM

P: 45

The opencircuit voltage does not increase linearly with field current.
If the field current is increased, the machine steel saturates and the opencircuit characteristic exhibits stagnationthe field current goes up the voltage does not. For low values of field current, the machine is unsaturated and the reactance value is referred to as the unsaturated reactance [Xsu]. The saturated reactance is defined as the reactance calculated at a field current which corresponds to rated armature voltage on the open circuit curve. 


#9
Jun2514, 08:50 AM

P: 8

https://docs.google.com/file/d/0B21H...T00/edit?pli=1 


Register to reply 
Related Discussions  
Electrical Engineering: Calculate the fault level for a 3Ø fault  Engineering, Comp Sci, & Technology Homework  0  
Trigonometry  solving force into components and determining magnitude of components  Introductory Physics Homework  4  
Energy of a sequence  absolutely summable sequence or square summable sequence  Engineering, Comp Sci, & Technology Homework  0  
Summer study in Australia vs Dual enrollemnt study at community collge?  Academic Guidance  2  
3 Phase System Line to Ground fault Fault current calculation  Engineering, Comp Sci, & Technology Homework  1 