Hi, We installed a chiller unit that had a working compressor. We turned it on, but nothing worked, after some fault finding, we found in the main panel, also newly installed, the neutral bridge was missing. This created problems as the neutrals on the chiller then created false highs on some phases and shorts to others... So a usually have 400V p-p, now 1 would read 100V, another 380V and another almost 600V. We found the missing neutral, added it, but now the compressor motor has burnt out. Could the missing break have caused this? Aside to that we found the overload was set to 9A when the motor was rated to 7A. Any thoughts?