I'm trying to design a double pipe heat exchanger for two different water lines. One line is chilled water of approximately 7degC and the other is chilled water return from an air handling unit, of around 12degC. I want to design this heat exchange for a capacity of approximately 22kW. The part I'm having trouble with is the heat transfer coefficients of the water. I'm planning to have a counter-current flow, with the 12degC on the inside copper pipe, with the chilled water running the opposite direction surrounding the other copper pipe. I've assumed there is sufficient insulation around the outside of the system so the overall system is adiabatic. I've tried a few different methods of finding the heat transfer coefficients. One way is simply looking them up, and another calculating them from the Reynold's number and Nusselt number. Both have given me very different answers. My objective is to calculate how long this heat exchanger needs to be for it to have an overall capacity of 22kW. The flow rate can be up to 8L/s and the pipe sizes have no real constraints.(adsbygoogle = window.adsbygoogle || []).push({});

Here's some pictures of what I've calculated and assumed

https://ibb.co/mxz0T5

https://ibb.co/f1GQvk

When looking up the heat transfer coefficients, on the engineering toolbox it listed the coefficients for water-copper-water as 340-455W/m^2K http://www.engineeringtoolbox.com/overall-heat-transfer-coefficients-d_284.html

From my calculations though I've found the coefficients to be 1189 and 823W/m^2K, which changes the length required from 104m to 41m with the calculated coefficients. The engineering toolbox coefficients assume a "practically still fluid", but my velocities are only 0.33m/s and 0.11m/s. This just seems like a very big difference in length required for such low velocities, so just wondering if I went wrong somewhere in my calculations.

One other question, when calculating h1 & h2, I've used the thermal conductivity of water rather than the copper pipe. Is this correct?

**Physics Forums | Science Articles, Homework Help, Discussion**

The friendliest, high quality science and math community on the planet! Everyone who loves science is here!

# Double pipe heat exchanger

Tags:

Have something to add?

Draft saved
Draft deleted

**Physics Forums | Science Articles, Homework Help, Discussion**