# How I can calculate the cv of a ball valve

by gabriel
Tags: ball, valve
 Share this thread:
 P: 10 Hi! I am working with ball valves and I need to calculate the cv for several sizes. I only knows the pressure drop expressed in terms of the "equivalent feet". Unfortunally, I do not have a lab to measure. thanks a lot!
 Sci Advisor P: 5,095 The equivalent length is $$L_{eq}=\frac{K_L D}{f}$$ where $$L_{eq}$$ is the equivalent length $$K_L$$ is loss coefficient $$D$$ is the flow diameter $$f$$ is the friction factor So it would appear that you would have to make assumptions of not only the friction factor, but also the loss coefficient. I would say that you are not going to get to the Cv from where you are with any accuracy. Honestly, you should be able to contact the valve manufacturer and they will give you the Cv. I don't know of a single valve maker that doesn't or won't give you that data. Perhaps if you tell us what brand and type of ball valve you have we can hunt the info down.
Sci Advisor
HW Helper
PF Gold
P: 2,907
Hi gabriel
 Honestly, you should be able to contact the valve manufacturer and they will give you the Cv. I don't know of a single valve maker that doesn't or won't give you that data.
Honestly, that's the right answer. "Ask the manufacturer."

I remember one or two very inexpensive ball valve manufacturers who didn't have that information though. They weren't industry quality valves, they were more like valves for home or garden use that didn't have a Cv rating. If that's the case, you can relate Cv to equivalent length as Fred was starting to discuss. Note that:
K = 891*d^4 / Cv^2
Where K = resistance coefficient referenced in Fred's post
d = inside diam (inches)

Now you can take Fred's equation and this one and you're left with one additional unknown, which is friction factor, f. Sorry, but you can't get any better than that. You have to make an assumption on f as Fred mentions.

The other way I'd suggest depends on whether or not this is a reduced port ball valve (ie: one that has a ball with an ID smaller than the ID of the pipe). If the ID of the ball is the same as the ID of the pipe, just neglect the valve altogether and assume it's a straight section of pipe. If the valve is a reduced port, calculate the resistance coefficient, K for a sudden contraction, and another for a sudden expansion, add them together, and relate that to Cv from the equation I gave above.

Attached is a paper that reviews some of this, and in which you can find sudden expansion and contraction coefficients.
Attached Files
 Pipe-Flo Pro.pdf (105.0 KB, 122 views)

 P: 10 How I can calculate the cv of a ball valve Many thanks for your answers, they were really helpful and also the pdf.

 Related Discussions Classical Physics 6 Engineering Systems & Design 10 Engineering, Comp Sci, & Technology Homework 3 General Physics 5 General Engineering 9