
#1
Jan2109, 09:39 AM

P: 7

I need to determine if a valve can handle a flow rate of 50 GPM, this valve being: 2/2 Way, Normally closed, w/ 2pilot control, and coupled solenoid.
I also need to determine pressure drop... it is a burkhert model  457361D the valve specs indicate: Cv = 35.1 pressure measurement = 0 145 psi if anyone can help, or push me in the right direction, thanks... 



#2
Jan2109, 11:08 AM

Sci Advisor
P: 5,095

The Cv is your main source of information. The Cv is, by definition, the amount of flow through the valve with a delta P across it of 1 psi. Most valve suppliers will give you a curve of Cv vs. % open. You can use the following equation to calculate the flow through given the following equation:
[tex]Cv = Q \sqrt{\frac{SG}{\Delta P}}[/tex] 



#3
Jan3009, 07:35 PM

P: 9

The equation given is generally correct as long as there is no choking, and the flow is laminar.
The ISA standard S75.01.01 gives extensive information on the subject. Also, the valve manufacturer should provide sizing information that will take that into account. www.ostand.com 



#4
Jan3009, 07:36 PM

P: 9

how to use flow rates (GPM) and pressure drop to determine if a valve is usefull
ooops I meant to say the flow must be TURBULENT.




#5
Jan3009, 09:06 PM

Sci Advisor
P: 2,283

CS 



#6
Jan3009, 09:29 PM

P: 9

It is part of the ISA S75.01.01 This is "the" standard of the valve industry.
Most references ignore this at their peril. Choking occurs when the pressure in the vena contracta within the valve drops to the vapor pressure of the liquid and vaporization occurs, preventing further flow increases, unless the inlet pressure is increased. Turbulent flow rather than laminar or transitional will pass the amount indicated by the equation that was quoted earlier. Otherwise the equation must be modified by a valve reynolds number factor which is =<1. Turbulent flow occurs when the valve reynolds number is 10,000. This is calculated by the equations in the ISA standard. If these factors are not checked for signifcant errors can occur in the calculation of flow or delta p. 



#7
Jan3009, 09:49 PM

P: 9

This might be of some use in understanding what I was trying to say, as it relates to turbulent flow.




#8
Feb209, 11:33 AM

P: 7

thanks for your help guys... I found what I needed a while ago, but your responses were appreciated



Register to reply 
Related Discussions  
How does a pressure reducing valve work?  General Engineering  12  
PRV valve pressure drop  Mechanical Engineering  5  
Bernoulli's Pressure Drop Segregated from Friction Pressure Drop  General Physics  7  
Pressure and flow rates  Introductory Physics Homework  1  
Determine Force/pressure from air flow?  Mechanical Engineering  10 