- #1

- 8

- 0

Also what temperatures should the cycle be designed for based on the contraints given?

- Thread starter TheDon
- Start date

- #1

- 8

- 0

Also what temperatures should the cycle be designed for based on the contraints given?

- #2

- 8

- 0

the fluid is r-134a also

- #3

Mech_Engineer

Science Advisor

Gold Member

- 2,572

- 172

- #4

- 8

- 0

heat transfer is next semester. The problem can get very indepth but the design is supposed to be simple. I just need to know what temperatures i should design it for and how to calculate the h for that above equation. I can find the mass flow rate from the eqn

Qin=m(h1-h4) since Qin is given but i got a flow rate of .0034 kg/s which seems very low using temperatures of 100.4F and -13F

- #5

Mech_Engineer

Science Advisor

Gold Member

- 2,572

- 172

What assumptions have you made to fix the states of the gas at states 1 & 4? Saturated vapor? Your application of the equation that determines the mass flow across the heat exchanger is correct, as long as you have properly fixed states 1 & 4 and looked up the correct enthalpy values.

- #6

- 8

- 0

State 1- sat vapor T= -25C i interpolated for h1, p1 and s1

State 2 s1=s2 T = 38C . i interpoated in superheated tables to get h2

state 3 sat liq 38C

State 4 h3=h4

i know how to go about the process i just need to double check on what temperatures to use and how to find the length of the condeser tube and size of the tube. I can use Qout=hA(/\T) to solve for L which comes from A=2piL but i cannot also find h. And the delta T is (Tfluid-Tsurroundings). How do I find the T fluid?

- #7

Mech_Engineer

Science Advisor

Gold Member

- 2,572

- 172

That's true, but you can't really choose any old arbitrary number. I suppose if you haven't taken heat transfer yet, this is the only way to do it though...But i heard from a few ppl that you have to choose temperatures above the hot region and below the cold region i believe due to efficiencies since no cycle is 100% efficient.

Are you supposed to calculate the convective coefficient (h) around the pipe even though you've never taken heat transfer, or are you given something to use?

- #8

- 8

- 0

- #9

- 8

- 0

A vapor compression regrigeration system using r134a is being designed for a household food freezer. The refrigeration system must maintain a temp. of 0F within the freezer compartment when the temp of the room is 90F. Under these conditions, the steady state heat transfer rate from the room into the freezer compartment is 1500btu/h. Specify operating pressures and temperatures at key points within the refrigeration system and estimate the refrigerant mass flow rate and compressor power required. Design for capacity factor of about 50%(i.e the compressor will run about 50% of the time). Select a compressor for the design from among the available sizes from suppliers. Select material and tube size for the condenser tubing, and estimate the total condenser tube length. Estimate the annual cost of operatin for the system.

- #10

Mech_Engineer

Science Advisor

Gold Member

- 2,572

- 172

Well, zooming you ahead about a semester into the future, here's how to calculate the convective coefficient around a horizontal tube:

First, calculate the Rayleigh number (dimensionless parameter):

Rayleigh Number-

[tex]Ra_{D}=\frac{g\beta\left(T_{s}-T_{inf}\right)}{\nu\alpha}[/tex]

Where g is gravity, [tex]\beta=1/T_{s}[/tex] for a perfect gas (T in kelvin), [tex]\nu[/tex] is the kinematic viscosity of air, and [tex]\alpha[/tex] is the thermal diffusivity of air.

Next, the Nusselt number (also dimensionless):

Nusselt number-

[tex]\overline{Nu}_{D}=\left\{0.60+\frac{0.387Ra_{D}^{1/6}}{\left[1+\left(0.559/Pr\right)^{9/16}\right]^{8/27}}\right\}^{2}[/tex]

Where the Prandtl number (Pr) is a propety of air, Pr=0.697 at 367K

Finally, the convective coefficient is:

[tex]\overline{h}=\frac{k}{D}\overline{Nu}_{D}[/tex]

Where k is the thermal conductivity of air

So, the heat loss per unit length of pipe is:

[tex]q'=\overline{h}*P*\left(T_{s}-T_{inf}\right)[/tex] (P is the perimeter of the pipe, pi times D)

Or heat loss over the length of the pipe is heat loss per unit length times the length of the pipe.

First, calculate the Rayleigh number (dimensionless parameter):

Rayleigh Number-

[tex]Ra_{D}=\frac{g\beta\left(T_{s}-T_{inf}\right)}{\nu\alpha}[/tex]

Where g is gravity, [tex]\beta=1/T_{s}[/tex] for a perfect gas (T in kelvin), [tex]\nu[/tex] is the kinematic viscosity of air, and [tex]\alpha[/tex] is the thermal diffusivity of air.

Next, the Nusselt number (also dimensionless):

Nusselt number-

[tex]\overline{Nu}_{D}=\left\{0.60+\frac{0.387Ra_{D}^{1/6}}{\left[1+\left(0.559/Pr\right)^{9/16}\right]^{8/27}}\right\}^{2}[/tex]

Where the Prandtl number (Pr) is a propety of air, Pr=0.697 at 367K

Finally, the convective coefficient is:

[tex]\overline{h}=\frac{k}{D}\overline{Nu}_{D}[/tex]

Where k is the thermal conductivity of air

So, the heat loss per unit length of pipe is:

[tex]q'=\overline{h}*P*\left(T_{s}-T_{inf}\right)[/tex] (P is the perimeter of the pipe, pi times D)

Or heat loss over the length of the pipe is heat loss per unit length times the length of the pipe.

Last edited:

- #11

- 8

- 0

does Pr vary depeding on what temperature it is at? if so is there a table to show these value

- #12

Mech_Engineer

Science Advisor

Gold Member

- 2,572

- 172

Pr does vary with temperature, I have a table in the back of my book. For 300K (approx 90 degrees F) [tex]Pr=0.707[/tex] for air. It is actually just a ratio of the kinematic viscosity and thermal diffusivity of air: http://en.wikipedia.org/wiki/Prandtl_numberdoes Pr vary depeding on what temperature it is at? if so is there a table to show these value

Additionally, [tex]\nu=15.89*10^{-6}\frac{m^{2}}{s}[/tex], [tex]\alpha=22.5*10^{-6}\frac{m^{2}}{s}[/tex], and [tex]k=26.3*10^{-3}\frac{W}{m*K}[/tex] at 300K for air.

Last edited:

- #13

- 8

- 0

would the eqn h=k/d work? i saw it in wikipedia

- #14

Mech_Engineer

Science Advisor

Gold Member

- 2,572

- 172

That sounds like a heat conduction equation to me, in which case no it will not work. Got a Wikipedia link?would the eqn h=k/d work? i saw it in wikipedia

Last edited:

- #15

Mech_Engineer

Science Advisor

Gold Member

- 2,572

- 172

[tex]Ra_{D}=\frac{g\beta\left(T_{s}-T_{inf}\right)D^{3}}{\nu\alpha}[/tex]

- #16

- 12,115

- 152

I'm sorry I can't help with the convection calculations, but don't you really want the compressor to handle 3000 btu/hr or 880 Watts?The problem states:

... Design for capacity factor of about 50%(i.e the compressor will run about 50% of the time)...

- #17

Mech_Engineer

Science Advisor

Gold Member

- 2,572

- 172

Yup, if the compressor is meant to have a 50% duty cycle, it will have to have twice the minimum required capacity.I'm sorry I can't help with the convection calculations, but don't you really want the compressor to handle 3000 btu/hr or 880 Watts?

It looks to me like the condenser tube length will have to be very long (on the order of a couple hundred feet) and fairly hot (around 340K) if you only consider it a cylindrical tube with no fins attached. This is obviously why real freezers' condensers are cooled with large heatsink arrays that maximize surface area to minimize fluid path and temperature difference required.

- #18

- 2

- 0

Thank you my friend on this subject interesting and wonderful

And I want to add some information on your subject

You will find information on this link

"[URL [Broken]

R-13 refrigerant

[/URL]

To benefit only

Thanks

And I want to add some information on your subject

You will find information on this link

"[URL [Broken]

R-13 refrigerant

[/URL]

To benefit only

Thanks

Last edited by a moderator:

- Replies
- 1

- Views
- 2K

- Replies
- 2

- Views
- 4K

- Replies
- 1

- Views
- 1K

- Replies
- 2

- Views
- 3K

- Replies
- 14

- Views
- 2K

- Last Post

- Replies
- 8

- Views
- 1K

- Last Post

- Replies
- 3

- Views
- 4K

- Last Post

- Replies
- 3

- Views
- 4K

- Last Post

- Replies
- 2

- Views
- 3K

- Last Post

- Replies
- 4

- Views
- 5K