# Calculating pressure at pressure relief valve outlet

• smims
In summary, the conversation discusses the calculation of discharge pressure at the vent exit of a tank with a Pressure Relief Valve (PRV) set at 30 PSIG and a capacity of 60,000 SATSTM. The steps for calculation are outlined, including specific volume of dry saturated steam, volume flow rate, and pressure drop. It is noted that the pressure at the outlet of the vent pipe will be equal to atmospheric pressure, unless critical flow conditions are present. The importance of using accurate density in calculating pressure drop is also emphasized.

#### smims

I have a tank which has a Pressure Relief Valve (PRV) connected to the atmospheric vent (Carbon steel with friction coefficient of 0.14). The PRV is opened at Set pressure of 30 PSIG and has a capacity of 60,000 SATSTM (I assumed it to be in lb/hr). I am trying to calculate the discharge pressure at the vent exit (opening).

The steps,

1. From steam table, specific volume of dry saturated steam at 30 PSIG = 9.5 cu.ft./lb
2. Calculating the volume flow rate at the exit = 60,000 x 9.5 = 570,000 cu.ft./hr = 158.33 cu.ft./sec
3. Calculating the nozzle outlet cross sectional area = 0.55 sq.ft. (Pipe nozzle diameter = 10 in = 0.83 ft)
4. Velocity at the exit = 158.33 x 0.55 = 290 ft/sec
5. Calculating pressure drop = (Friction coefficient/2) x (Pipe Length/Pipe Diameter) x (Velocity squared/gravity) = 0.14 x (10 ft /0.83 ft) x (290.35x290.35/32.17) = 2201 ft = 953 psi (Impossible!)

here is the excel file http://www.filedropper.com/prv_1

If I include the density in the above pressure drop calculation, the unit turns out to be in PSI than ft. But then I found no such equation that includes the density in calculating the pressure drop. What am I missing? Thanks.

Last edited:
Pressure at the outlet of the vent pipe will be equal to atmospheric pressure - 0 psig .

If you are working this as an exercise then Nidum can be considered close enough. If this is a real relief valve application you are better (and much safer) relying on a reliable supplier to do the calculation for you. Pressure at the outlet nozzle can be well above atmospheric pressure because a pressurized area will form at the outlet under actual relief.

I used a large Friction coefficient (3.5E-06 is the right one).
The pressure turned out to be 0.15 PSIG. So Nidum is right.

It's worth noting that it is possible for the pressure at your vent outlet to be higher than atmospheric pressure if you have critical flow. i.e mach 1 conditions at vent outlet. For the vent pressure drop you need to use the density at downstream pressure which will be be the backpressure created during relief which will less than the set pressure. It seems you have used the upstream density for your pressure drop calcs. First you need to check if the flow is critical at the vent outlet. If not your pressure at the outlet will be atmospheric. If it is then your pressure drop will be higher than atmospheric. Then you need to back calculate the pressure back to the relief valve outlet.

## 1. What is the formula for calculating pressure at pressure relief valve outlet?

The formula for calculating pressure at pressure relief valve outlet is P = (F x L) / A, where P is pressure, F is force, L is length, and A is the area of the valve outlet.

## 2. How do you determine the force applied to the pressure relief valve?

The force applied to the pressure relief valve can be determined by multiplying the pressure inside the valve by the area of the valve outlet.

## 3. What factors affect the pressure at the pressure relief valve outlet?

The pressure at the pressure relief valve outlet can be affected by factors such as the flow rate of the fluid, the type and size of the relief valve, and the temperature and density of the fluid.

## 4. Why is it important to calculate the pressure at the pressure relief valve outlet?

Calculating the pressure at the pressure relief valve outlet is important in ensuring the safety and proper functioning of the valve. It allows for the determination of the appropriate pressure setting for the valve to prevent overpressure and potential equipment failure.

## 5. Are there any safety precautions to consider when calculating pressure at the pressure relief valve outlet?

Yes, it is important to follow proper safety protocols when calculating pressure at the pressure relief valve outlet. This may include wearing appropriate protective gear and ensuring the valve is properly installed and maintained. It is also important to use accurate measurements and follow the correct formula to avoid any potential hazards.