Hey.(adsbygoogle = window.adsbygoogle || []).push({});

If i Have a 3x400VAC system, and I want to calculate the voltage drop over the cable "vectorially" - or what you call it :) - how do I do this?

U.nominal=400V

I have tried this method:

[itex]\Delta[/itex]U.conductor=I.1*Z.cable1+I.2*Z.cable2+etc. and then I will have to find the new voltage ->

[itex]\Delta[/itex]U.phase=U.conductor*[itex]\sqrt{3}[/itex]

U.new=U.nominal-[itex]\Delta[/itex]U.phase

When I'm calculating this with angles, I actually get a higher voltage, after the voltage drop :D

The voltage drop is cause by a electrical motor starting.

In school we learn it this way:

[itex]\varphi[/itex].motor=80 degrees

U.new=U.nominal-[itex]\sqrt{3}[/itex]*I1*Length.cable1*(R.cable1*cos[itex]\varphi[/itex]+X.cable1*sin[itex]\varphi[/itex])+[itex]\sqrt{3}[/itex]*I2*Length.cable2(R.cable2*cos[itex]\varphi[/itex]+X.cable2*sin[itex]\varphi[/itex])+etc.

But that is not with vectors.

Hope you understand?

Thanks in advance.

**Physics Forums - The Fusion of Science and Community**

The friendliest, high quality science and math community on the planet! Everyone who loves science is here!

# Calculating voltage drops in cables with vectors?

Loading...

Similar Threads - Calculating voltage drops | Date |
---|---|

How to calculate voltage drop | Feb 28, 2018 |

Voltage drop calculations for CCVT's and Current TF's? | Oct 21, 2015 |

Overall Power Factor of three motors for transformer voltage drop calculation | Feb 9, 2015 |

Need to calculate the resistance accross membrane in water | Jan 21, 2015 |

I don't understand how I am "calculating for the voltage drop" | Sep 1, 2014 |

**Physics Forums - The Fusion of Science and Community**