- #1

- 13

- 0

this is not academic, i need to calculate bus bar current and 72M length which is fixed and i need wall thickness and inner and outer dia ?

thanks

You are using an out of date browser. It may not display this or other websites correctly.

You should upgrade or use an alternative browser.

You should upgrade or use an alternative browser.

- Thread starter muet
- Start date

- #1

- 13

- 0

this is not academic, i need to calculate bus bar current and 72M length which is fixed and i need wall thickness and inner and outer dia ?

thanks

- #2

Staff Emeritus

- 11,211

- 8,623

There are many sources of this information including

http://www.copper.org/applications/electrical/busbar/bus_table3.html

- #3

- 13

- 0

thanks anorlunda,yes i searched entire internet. and i found them. But. Problem is that. I am confused that my power which is to transfer and length 72m can suport that and my voltage and friquency and we have to connect 04 Stepup transformers.,selected bus bar will compatible with that much power and current ?

There are many sources of this information including

http://www.copper.org/applications/electrical/busbar/bus_table3.html

Last edited:

- #4

Staff Emeritus

- 11,211

- 8,623

Don't you mean MW, not MWh?250 MWh

I don't understand that phrase.from each 60mw 04 transformers

Voltage and frequency don't matter, only amps and temperature. For example, you can transfer up to 199 amps, with a 65 degree C temperature rise, using 1/16 inch (1.6 mm) thick, 1/2 inch (13 mm) diameter bus bar. The table in the link provided gives similar answers for many ampere ratings.

- #5

- 13

- 0

we have 60MVA 04Don't you mean MW, not MWh?

I don't understand that phrase.

Voltage and frequency don't matter, only amps and temperature. For example, you can transfer up to 199 amps, with a 65 degree C temperature rise, using 1/16 inch (1.6 mm) thick, 1/2 inch (13 mm) diameter bus bar. The table in the link provided gives similar answers for many ampere ratings.

Transformers which are going to connect. And we have to transfer almost 250 MW power at 132kv voltage ? Busbar

have to carry this much power all the time .

- #6

Staff Emeritus

- 11,211

- 8,623

250 MW power at 132kv voltage

Can you calculate the current from that data? If yes, what more do you need?

- #7

- 13

- 0

ok. I can calculate 250 MW at 132kv current. But i want to know. That bus bars are come in small sections which are going to connect and formed one 72m bare per phase. So all small bars have to carry that much current or combine of them say 72m single bar. ?Can you calculate the current from that data? If yes, what more do you need?

Last edited:

- #8

Staff Emeritus

- 11,211

- 8,623

Since bus bars are not expensive, it might be smart to buy some rated two times the amount you calculate.

- #9

- 13

- 0

Since bus bars are not expensive, it might be smart to buy some rated two times the amount you calculate.

thanks man . but i am still confused. that my bus bar total length is 72 m / phase and they might come in 12m small parts 6 parts per phase. are they have to carry that much current individually or combine of them ?,

- #10

Staff Emeritus

- 11,211

- 8,623

The total length, and the number of short pieces doesn't matter.

- #11

- 13

- 0

The total length, and the number of short pieces doesn't matter.

means i have 12 m bar and 72m bar both have same rise of temperature at same current carrying ?

- #12

- 13

- 0

The total length, and the number of short pieces doesn't matter.

thanks anorlunda for informative conversation . we are gating 12m Bus bars total length of 72m per phase, and Dia is 80mm and wall thikness 8mm which will be carry upto 2500 A current at 85c temp ,

- #13

- 550

- 149

First of all I should recommend you to take an experimented engineer to check all your calculation. What you could get here it is a general information.

The busbar maximum temperature for steady state load it is not the single criterion.

The actual calculation involved static and dynamic load on busbar, insulators and other accessories.

The busbar system has to withstand short-circuit current thermal and electromechanical effect [See IEC 60865-1,2 for instance] wind, ice and earthquake effect.

Share:

- Replies
- 14

- Views
- 1K

- Replies
- 16

- Views
- 2K

- Replies
- 37

- Views
- 1K

- Replies
- 17

- Views
- 865

- Replies
- 19

- Views
- 721

- Replies
- 10

- Views
- 872

- Replies
- 42

- Views
- 385

- Replies
- 12

- Views
- 628

- Replies
- 14

- Views
- 513

- Replies
- 13

- Views
- 386