# What factors affect heat rejection in vacuum pump systems?

• russ_watters
In summary, the vendor told me to figure 2,500 BTU/hr/hp, but I don't think that's true. The new pumps are rotary vane, air-cooled, so they will reject heat to the space.
russ_watters
Mentor
TL;DR Summary
How does vacuum pump heat rejection vary with flow rate/load?
I'm working on a project to replace a couple of vacuum pump skids for a lab campus. The existing pumps are water-cooled, liquid-ring pumps. Since they are water cooled, there is effectively no heat rejection into the mechanical room(s) except through un-insulated exhaust pipes. The new pumps are rotary vane, air-cooled, so they will reject heat to the space. So, how much?

The vendor told me to figure 2,500 BTU/hr/hp, which is just another way of saying "all of it". But I don't think that's true. A couple of issues:

1. The vacuum exhaust is ducted (piped) out of the building. Now, since this volume is small and the piping isn't insulated, I'm comfortable saying it still gets rejected into the room. But it would still be nice to know what fraction goes into the airstream. But there may not be an easy way to find this out.

2. I'm pretty sure the heat rejection (and pump horsepower) varies with load, but I'm not certain of that or exactly how. I'm more familiar with compressors, so I'll use an analogy/comparison, to make sure I understand, and I'm looking for confirmation/correction:

Picture a reciprocating compressor (I assume the same thermodynamics applies to a rotary compressor/pump). It's just a piston in a cylinder. As the piston squeezes the air, the air heats up. A certain fraction of the work is held in the compressed air and the rest is released as heat. The amount of lost heat is significant, but it isn't 100%. In addition, the heat rejection changes with load. Consider the firsts stroke of the compressor to pump-up a surge tank/system. The gauge pressure is zero and the pressure rise/compression is pretty close to zero. The compression stroke has nearly zero force behind it, so the work done is near zero and the heat of compression is near zero. As the system pumps up, the pressure rises, force on the piston rises, and work done with each stroke rises. The work done and heat rejection increases as the system is pumped-up to operating pressure. Maximum work is done on the last stroke, and the system if operating at continuous maximum flow operates at maximum power and maximum heat rejection.

Assuming the above is correct:
[As I type this, I realize this is going in a different direction than I thought...]

The vacuum pump kind of works in reverse, but not exactly. The first stroke also does near zero work. But after that, we have two competing parameters:
1. Pressure difference increases with each stroke.
2. Input mass decreases with each stroke.

From this, I conclude: Peak work (power) for a vacuum pump system occurs somewhere in the middle of pump-down, when there is a significant pressure difference, but still a significant mass flow rate. Heat rejection increases as a fraction of power input as the system is pumped down. But once the system is pumped-down, the work done on the last stroke is effectively zero; There is a large compression ratio, but effectively zero volumetric flow rate. And even at maximum working flow rate, the power is still effectively zero.

Thoughts?

Lnewqban
russ_watters said:
Heat rejection increases as a fraction of power input as the system is pumped down. But once the system is pumped-down, the work done on the last stroke is effectively zero; There is a large compression ratio, but effectively zero volumetric flow rate. And even at maximum working flow rate, the power is still effectively zero.
Here's where I think I may have gone wrong: when two parameters are trending in opposite directions, intuition can fail you about what happens when you multiply them together. The product may go up or it may go down. I think I will probably need to do the calculations to find out...unless someone already knows the answer to this.

I agree with all your reasoning above.
Sorry, I can't help in this case, I have experience only with portable vacuum pumps, which don't produce significant amount of heat from the pump itself.

If the old and new pumps have comparable capacities, and if you could visit the old installation, perhaps you could estimate how much heat the liquid cooler could have been moving out of the room.
If the system is still operational, measuring the Amps actually used by the motors could give you another estimate.

The estimate of heat based on HP of the motors should consider that only a fraction of HP listed in the nameplate will be used, and even that amount will vary with time of operation and level of achieved vacuum.
Again, measuring the actual Amps flowing into the mechanical room, if at all possible, is a more conservative way of sizing cooling or ventilation of that room.

If the outdoor/indoor delta temperature and humidity is expected to be big sometimes, it may be a good idea to insulate the exhaust ducts, just to prevent condensation on the naked metal surfaces when flow is minimum or zero.

russ_watters
I agree with your reasoning. I suspect that the Vendor's pump curve will give you motor power (vs Pressure, Flow). That isn't everything that you'd like to have, but it will narrow things down. A 'pump temp' plot might also be helpful. 'Running Friction' can be non-trivial with vane pumps - the 'no work' power/heating may be higher than you expect.

Lnewqban and russ_watters

## What is a vacuum pump and how does it work?

A vacuum pump is a device that removes gas molecules from a sealed volume in order to create a partial vacuum. It works by creating a low pressure area in the pump, causing gas molecules to move from the higher pressure area into the pump, thus creating a vacuum.

## Why is heat rejection important in vacuum pumps?

Heat rejection is important in vacuum pumps because the process of creating a vacuum generates heat, which can lead to overheating and damage to the pump. Heat rejection helps to dissipate this excess heat and maintain the proper operating temperature of the pump.

## What factors affect heat rejection in vacuum pumps?

The factors that affect heat rejection in vacuum pumps include the type and size of the pump, the type of gas being pumped, the ambient temperature, and the operating pressure. Additionally, the design and efficiency of the heat rejection system also play a role in the overall heat rejection of the pump.

## How can heat rejection be improved in vacuum pumps?

There are several ways to improve heat rejection in vacuum pumps, such as increasing the surface area of the heat rejection system, using more efficient cooling methods (such as liquid cooling), and optimizing the design of the pump to reduce heat generation. Regular maintenance and cleaning of the pump can also help to improve heat rejection.

## What are the consequences of inadequate heat rejection in vacuum pumps?

Inadequate heat rejection in vacuum pumps can lead to overheating, which can cause damage to the pump and decrease its efficiency. This can result in increased energy consumption, decreased pump performance, and potentially costly repairs or replacements. It is important to ensure proper heat rejection in vacuum pumps to maintain their optimal functioning and prolong their lifespan.

• Mechanical Engineering
Replies
1
Views
2K
• Mechanical Engineering
Replies
15
Views
972
• Mechanical Engineering
Replies
4
Views
2K
• Mechanical Engineering
Replies
6
Views
1K
• Mechanical Engineering
Replies
9
Views
3K
• Mechanical Engineering
Replies
5
Views
276
• Mechanical Engineering
Replies
13
Views
2K
• Mechanical Engineering
Replies
1
Views
2K
• Classical Physics
Replies
7
Views
1K
• Mechanical Engineering
Replies
13
Views
455