I am using the "Three-Phase PI Section Line" Matlab-Simulink block from Simpowersystems blockset for modelling an electric power system transmission line.(adsbygoogle = window.adsbygoogle || []).push({});

I had obtained the data from a research paper regarding the transmission line specifications (provided as sequence values).

Since I am trying to do actual impedance calculations of each phase for distance protection & fault location purposes, I tried to compute the variation of per phase impedance using a Matlab program (given below).

The program takes the system data of the transmission line (which are given in unit/km), which can be used as parameters for the Simulink 3 phase pi-section block.Code (Text):clear all; clc;close all;

a=exp(deg2rad(120)*1j); %% a = -0.5000 + 0.8660j

A = [1 1 1; 1 a^2 a; 1 a a^2]; %% Matrix for Symmetrical component transformation

Fo = 60;

%% Line Specification using sequence values (taken from paper)

R10 = [0.0317 0.3192]; L10 = [0.3204 1.0083]./(2*pi*60) ; C10 = [10.838e-9 7.6493e-9];

Distance = 1:150; %% in km

for k = 1:length(Distance)

R10 = R10*Distance(k); L10 = L10*Distance(k); C10 = C10*Distance(k);

XL10 = (2*pi*Fo)*L10; XC10 = 1./((2*pi*Fo)*C10);

Z10 = R10 + 1j*( XL10 - XC10 );

Z0(k) = Z10(2); Z1(k) = Z10(1); Z2(k) = Z1(k);

Z012 = [Z0(k) 0 0; 0 Z1(k) 0; 0 0 Z2(k)];

Zabc = A*Z012*((1/3)*(A'));

Zs(k) = Zabc(1); Zm(k) = Zabc(2);

end

figure(1);subplot(2,1,1);plot(Distance,real(Z0));subplot(2,1,2);plot(Distance,imag(Z0));

figure(2);subplot(2,1,1);plot(Distance,real(Z1));subplot(2,1,2);plot(Distance,imag(Z1));

figure(3);subplot(2,1,1);plot(Distance,real(Zs));subplot(2,1,2);plot(Distance,imag(Zs));

figure(4);subplot(2,1,1);plot(Distance,real(Zm));subplot(2,1,2);plot(Distance,imag(Zm));

The distance is multiplied to the data to get the actual values.

The impedances are computed, the sequence impedances and the per phase impedances are found out. The values of resistance and reactance are computed from the real part and imaginary part respectively. This operation is done for various distances and the plot shows that.

I find that the values plot rise to very high values (order of 1e200). How can current flow if impedance is so high ? If the system data is inappropriate, please tell me why.

Please suggest the reason for such a problem and how can I overcome it?

Thanks in advance :)

**Physics Forums | Science Articles, Homework Help, Discussion**

The friendliest, high quality science and math community on the planet! Everyone who loves science is here!

# Three Phase pi-section model of power system transmission lines

**Physics Forums | Science Articles, Homework Help, Discussion**