# Calculate pressure loss due to bends in a pipe?

1. Dec 28, 2011

### daftdave11

how we doing i found the following information regarding finding the pressure drop in a pipe due to 90° bends. i was wondering could this be adapted for say a bend of 60° or 45°. what would be needed to change to the below information to allow this to happen?? thanking ou in advance. this would be a great help to me if i could find the solution to this.. thanks

K_B = (n-1)(.25*\pi f_T \frac{r}{d} + .5 K) + K
Where:
K_B = Resistance coefficient for overall pipe bend.
n = # of 90° bends (for a single 180° bend, n=2).
\pi = well......pi
f_T = Friction factor in turbulent zone.
r= radius of bend (in same units as d).
d= inside diameter of pipe (same unit as r).
K= Loss coefficient for a 90° bend based on table below.

90° Bend Loss Coefficients:
r/d = 1, K = 20f_T
r/d = 1.5, K = 14f_T
r/d = 2, K = 12f_T
r/d = 3, K = 12f_T
r/d = 4, K = 14f_T
r/d = 6, K = 17f_T
r/d = 8, K = 24f_T
r/d = 10, K = 30f_T
r/d = 12, K = 34f_T
r/d = 14, K = 38f_T
r/d = 16, K = 42f_T
r/d = 20, K = 50f_T

2. Dec 29, 2011

### daftdave11

anyone??

3. Dec 29, 2011

### Q_Goest

You have the values given by the Crane paper for the total resistance of a 90 degree bend. You can multiply those resistance values by the following equation to get the resistance for all other bends between 0 and 180 degrees:
y = 1.838E-7*A3 - 8.756E-5*A2+1.748E-2*A
Where y = angle factor
A = angle of pipe bend from 0 to 180 degrees

This equation comes from a graph out of a book on fluid flow from a company I used to work for. I took the graph and did a curve fit to it. You should find that at 90 degrees the angle factor comes to 1.00 and at 180 degrees, the angle factor comes to 1.38.

Know someone interested in this topic? Share this thread via Reddit, Google+, Twitter, or Facebook