Hi,(adsbygoogle = window.adsbygoogle || []).push({});

I'm trying to perform a short circuit fault calculation on this transformer and load I have when a 3 phase bolted short (worse case) occurs.

The transformer specs are below:

Z(transformer)=5%, Z(cable)= .00306 + j.0027, Delta/Star 6.6kV/400V

I can understand calculating the short circuit available current at the load:

Ifault(load) = Vphase/Z(transformer)

where Z(transformer) is the impedance of one winding, and the voltage across it would be 400/1.73 ~=230V

Ifault(load) = 230/.05

= 4.6kA

Now calculating the fault down at the load is where I get a little confused:

The example I'm following states that the load current fault for a 3 phase bolted short is:

Ifault(load) = Vphase/(Z(transformer) + Z(cable))

My only guess/understanding of why they use Vphase is that Vphase represents the voltage drop from the neutral (mid point) of the WYE transformer to the end of 1 phase? I've drawn a diagram to help clarify what I mean, its hosted at:

http://img83.imageshack.us/my.php?image=61884112bb8.jpg

Can someone please explain to me why they use Vphase in the load fault calculation?

**Physics Forums | Science Articles, Homework Help, Discussion**

Join Physics Forums Today!

The friendliest, high quality science and math community on the planet! Everyone who loves science is here!

The friendliest, high quality science and math community on the planet! Everyone who loves science is here!

# Transformer short circuit fault calculation clarification

**Physics Forums | Science Articles, Homework Help, Discussion**